Inspection & Overhaul (Urgent Service)
HTC Condensing Steam turbine - Gear and Generator 9.9 MW.
IEC Sakaeo 1 Co.,Ltd.
Found seal strips of turbine rotor balance piston damage.
Remove originat seal strips for replacement
Assembling new seal strips.
M/C finish size new seal strips of turbine rotor job done.
The original pad plane bearing DE & NDE damaged,
it needs to be re-babitt.
Re-babbitt pad plane bearing for under size(DE & NDE) job done
The original Thrust pad bearing NDE & DE for turbine rotor damage,
it needs to re-babbitt
Re-babbitt pad thrust bearing for under size action end job done
The original Labyrinth oil guard NDE for turbine rotor damage,
Replace new labyrinth oil guard for turbine NDE job done.